What skills to learn, what tools to get
4 posts • Page 1 of 1
Thanks for the reply Ego. When I got home after that, the compressor was on without me having to do anything. The following day it was cold out, but when it was hot again there was a clear difference between thermostat set temperature and measured temp. That's why I'm thinking its an issue with the zone dampers or board.
Here we go again. Air handler is on. Compressor is on. The conduit (the copper pipe external to the air handler) is cool to the touch. But no cool air is coming out of the vents. It's gotta be the zone board or the damper. How do I proceed?